Expert Electricians in Buford, Georgia
Are you tired of dealing with flickering lights? Have you noticed a burning smell coming from your electrical outlets? Has a sudden circuit shortage left you in the dark? In today’s day and age, even minor electrical problems can become a nuisance. At R.S. Andrews, we never want you to feel inconvenienced in your own Buford home, which is why nothing but the absolute best electrical service will suffice.
You need a team of professionals that is dependable, skilled, and tuned in to providing you exceptional service across the board. Our certified electricians lead the industry in technical knowledge and training, ensuring you get the attention you need!
No matter the electrical problem you’ve encountered in Buford, Georgia, contact the electricians at R.S. Andrews.
Electrical Services with R.S. Andrews
We’ve tailored our electrical services to be all-encompassing so we can be sure to meet your every need and expectation. When you need residential or commercial electrical services in Buford, you can be confident in looking to R.S. Andrews for:
- Electrical installation
- Electrical repair
- Electrical troubleshooting
- Service panel upgrades
- Smoke detector inspection
- Smoke detector installation
- Surge protection
- Circuit breakers
Whether it be repairs, installations, or maintenance, R.S. Andrews can provide assistance! We’ve dedicated ourselves to providing services that Buford homeowners can trust, bringing you top-quality in both products and skill to ensure your electrical projects are done quickly, efficiently, and perfectly!
Need electricians in Buford? Contact our team today for the answer to all of your electrical needs! You can reach us online, or over the phone at 770-913-6412.
Buford Electrical & Wiring Repair
Electricity is a fickle beast, and one that requires an electrician with the confidence and knowledge necessary to ensure your repairs go off without a hitch. You can count on our Buford electricians for all of your repair needs. Not sure when you may need repairs? Keep an eye out for these sure signs that you need electrical repair:
- Appliances generating unnatural heat. It’s fairly normal for machines and appliances to stay slightly warm during operation, but if you notice equipment getting warmer than usual, or even hot to the touch, there’s likely an issue with your wiring.
- Over-frequent flickering. A little flicker now and then is natural, and common to all homes. But if you notice a frequent or consistent flicker that doesn’t seem tied to major machinery kicking into action, you may have an issue with your wiring, breaker box, or appliance.
- Sparking. Outlets that spark, or sparking coming from fixtures is a sure sign of arcing or a weak ground, both of which should be addressed immediately!
- Burning, charring or “ozone” smells. If you notice any smell resembling burning coming from your panel or wires, cut power to your home and contact a professional immediately. This is a very serious issue, and should be handled right away!
If you’ve noticed any of these warning signs in your Buford home, give R.S. Andrews a call at 770-913-6412 immediately!
Buford Electrical Installations & Replacement
Part of our personal mission as a business is to provide only the finest quality products for installation or replacement in your home. Contact our team of Buford electricians today for any project you’re planning involving electricity. We’ve handled it all, and guarantee complete satisfaction on all of our work!
Why Choose an Electrician from R.S. Andrews?
You can trust more than just our good word at R.S. Andrews. All of our work comes fully guaranteed, both to provide confidence for you, and as a way to show pride in our work for ourselves. We choose only the finest electricians to provide our consumers with electrical services, choosing based not only on skill and knowledge, but on integrity, honesty, and friendliness as well!
Choose the service you can trust with R.S. Andrews today. Contact us to learn more about how our Buford electricians can help you, or to schedule an appointment!
for Buford, GA
Prompt and competent
Keith - Buford, GA
Highly competent and on time. Technician quickly assessed the difficulty and repaired the water line break. I would use them again.
Great and professional service
Mernoosh - Buford, GA
Professional, caring, and Awesome customer service
Top Notch Service
Kaitlin - Buford, GA
As always - top notch service and speed in resolution of the issue
Response from RS Andrews:
Thank you very much for your review!
Nicole - Buford, GA
Response from RS Andrews:
Thank you very much for your review!
linda - Buford, GA
Response from RS Andrews:
Thank you for your review!
Chris - Buford, GA
RS Andrews is always on time, and the people they send to your house are smart and knowledgable. I have used them for over 5 years now, and I will continue to use them because of the quality of service they provide.
Water leak, Installed new Filter saturated and dirty, Removed cleaned water from aux pan Monitor and balance refrigerant levels Low 112 High 285 SH 12 Sub 8Made Ms wolf aware might need new TXV but system operating properly at time after filter change Ms will keep eye on system and call if issue. Also made aware basement has one main return if want all rooms temperature same need to leave doors open or add returns.
Drain Line Repair HVAC Smiley Diagnostic Club
No basementFound clogged drain flushed out and removed water from drain pan made Cleint aware insulation saturated will keep dripping tell dries out cycled basement system operating properly Refrigerant levels L 113 SH 20 H 324 Sub 10 Found duct work block by items on top made aware could cause damage to duct work Replace air cleaner medias on main and upstairs levels very dirty Rinsed condenser coil on upstairs system suggested chemical cleaning T-Stat set to 66 upstairs unit struggling to keep temperature installed by reliable Made aware appointment under load set at 66? unit running all day will not reach set temperature
Poor cooling, Complaint Upstairs front bedroom (daughter) not getting enough air flow to cool roomOptions #1 Best solution reduct and zone system for total comfort $2895-3876#2 Reconfigure duct work to balance air flow to kids bedrooms $725 ($650 with club) Run new dedicated duct Remove old and cap off Need 1 8" duct run split into 2 6" ducts to bedrooms and secure
No cool, Upstairs system, Found condenser fan motor overheated due to shorted run capacitor system is 13 years old suggested upgradingInstalled new capacitor 35/5 Motor struggling to start Tested Motor running @1.3 amps (1.0 amp max could fail) Found low refrigerant super heat at 42 low signs of leak Recharge and balance refrigerant levels Low 70 psig Superheat 10'F High 212 psig Sub Cool 5'F Cleint aware system leaking refrigerant wants temporary fix **No warranty on refrigerant ** Measure temperature difference 18'F Outdoor temp 86'FClient Aware system needs further attention for permanent fix/repair also made aware system can freeze and leak water causing property damage Suggested upgrading equipment
Furnished, wired, and installed an outlet over the fireplace for a tv. Performed panel maintenance and tightened all connections. Used the customers wood to screw back the Sheetrock that was cut. We are not responsible for patching and painting said Sheetrock.
We furnished, wired, and replaced the smoke detector by the master bedroom on the second floor. The existing one was not sending a signal out, as found out by the home inspector. We tested all smoke detectors and they all work as they should now. We furnished, wired, and installed a bond wire from the main disconnect at the meter, to the gas line. This is to bond the csst as per home inspector.
U/S AC. Found low in freon added 2# of freon with NO warranties. 2.5 ton trane up flow in attic from 1996 recommend replacing system due to age. AC is operating at this time 75 psig at 12*SH.
Removed obstruction from garbage disposal. Tested OK.
Repaired main water service in the ground after meter. Removed PVC 1 foot section and installed PEX pipe with approved adopters. Tested OK.
Opened ceiling where water was dripping through Sheetrock and cabinet to find 1/2 inch copper water pipe feed to toilet had a pin hole leak.Removed section of pipe from leak up to toilet with new shut off valve and supply for toilet. No obvious cause for the leak there was nothing rubbing or touching pipe in this spot.
Came out to inspect grounding system and main electrical panel in home. After inspection determined the grounding system is partially complete and not up to current code. Water system in home is bonded as well as hot and cold sides, ground rods were not installed properly. Installed 2 new ground rods with continuous line to main disconnect to complete grounding system. Inspection of electrical panel found no problems and working properly.
Cabled master bathroom shower drain to clear stoppage. Tested OK.
Completed Air Conditioner preventative maintenance on two units.
Replaced cartridges to lavatory in hallway bathroom and with the customer to show all is good now.Checked pressure to house at 65 lbs.
Estimate for replacement of RHEEM water heater 50 gallon natural gas in garage labor material with expansion tank and water heater pan.Replace fill valve and flapper in two toilets. Install hose clamp on inst hot vent hose $0.00 total for all work.
Completed Air Conditioner preventative maintenance on one unit.
Completed Air Conditioner preventative maintenance on three units.
Estimate to upgrade service to 400 amp re-device of home 4900+ sq ft adding 9 smoke detectors, 1 per bedroom per code, and 1 in garage with living space above per code,and replacing 4 existing smoke detectors that are over 10 years old.
installed 50 gallon natural gas water heater with replacement thermal expansion tank.Removed old water heater for disposal.
Replaced fill valve, flapper and supply Line upstairs hall bath toilet.
customer said too much ice build up on unit had to turn off and remove ice. Found timer on defrost 120 minutes. Inspect defrost board speed up all ok. Removed power to outside unit and reset defrost board to every 30 minute run time. reconnected power. Let unit run 115 and 325 with 9 degree sc . unit operates normal. Did not find any trace of inordinate substance. we had unusual colder than normal weather. inside is non program Honeywell Tstat.
Unit not heating and making a loud noise.Found unit over heating due blower motor seizing up and blower motor wheel coming apart in very bad condition , Also a lot of build up in furnace burner assembly and heat exchanger compartment may cause combustion issues .Tried breaking free motor and tightened blower wheel hub loose/broken won't operate properly will cause over heating.suggested not to operate potential hazard and carbon monoxide detectors. Furnace is 30 years old Recommend upgrading left quote on repair options and upgrading (no guarantee parts available 30 years old).
Free second opinion on replacement of two unit. Found Both units working properly at time .
Warranty call: The gas Furnace Comfort maker is not working Properly on Heat Mode Due to Bad Pressure Switch and Bad ignition module control. The heat mode is working on Short cycling. Due to Aged and conditions I recommend to replaced the gas Furnace ASAP. Note. Costumer is aware of the problems on the unit.