Buford’s HVAC Company
Choose R.S. Andrews for Heating & Cooling Services in Buford
Imagine your Buford home without heating or cooling. Not too comfortable, right? That’s where R.S. Andrews can help. We are the area’s leading HVAC experts—so you can rest easy knowing a professional is on the job when any of your home systems break down or if you just need to replace old, malfunctioning equipment.
When you need a new HVAC system installed or an older system replaced, count on the professionals at R.S. Andrews. We’ve been working with HVAC systems throughout Buford for more than 50 years—contact us!
HVAC Installation in Buford
New HVAC installations present a wide variety of options that can save you money on your power bills and reduce the amount of HVAC maintenance and service that will ultimately be required over the life of your new unit. If you want to upgrade your existing system instead, options like adding heat pumps, two-stage furnaces, air-to-heat exchangers (HRVs), and programmable thermostats can all go a long way toward increasing efficiency and extending the life expectancy of your system.
No matter the HVAC system/product you need installed in Buford, R.S. Andrews can help. We have experience installing:
For all your HVAC installation needs in the Buford area, choose R.S. Andrews. Contact us today!
Heating & Cooling Maintenance in Buford
In order to get the most out of your equipment, we highly recommend regular HVAC maintenance. Many times, small timely adjustments and filter changes that are done on a regular basis can wind up saving you from breakdowns that always seem to occur right when you need your system the most.
Trust R.S. Andrews for high quality HVAC maintenance for the following systems in Buford:
The Smiley Advantage Maintenance Plan
Our technicians estimate that 82 percent of the repairs they see may have been eliminated or reduced by a regular tune-up program. Changing your air filters monthly is a step in the right direction, but it just isn’t enough. Modern HVAC systems have an advanced electronic system which requires cleaning and inspection from the inside out to ensure that every piece is properly calibrated and running efficiently – a task best left to a trained professional. Click here to learn about the benefits of our Smiley Advantage Plan.
Call R.S. Andrews at 770-913-6412, and one of our HVAC professionals will be happy to answer any and all of your HVAC questions and fulfill whatever needs you have for your HVAC system.
HVAC System Repair in Buford
There’s nothing worse than an inoperable heating or cooling system. They never seem to give out at a time that would be convenient for you, don’t you think? You air conditioner will probably break on the hottest day of the year, and vice versa for your heating system. For reliable HVAC repair in Buford, you can count on R.S. Andrews.
Our team has experience repairing the following systems:
Contact R.S. Andrews for HVAC repair—no matter the time or day, you can count on us. We provide 24 hour emergency HVAC repair in Buford.
Indoor Air Quality in Buford
We’ve found that many homes in Buford face significant indoor air quality issues as a result of the seasonal high humidity in our area, which creates conditions ripe for mold and mildew growth in both old and new HVAC systems. Our HVAC technicians can help you determine which strategies will work best for neutralizing airborne particulates in your Buford home, which often involves a combination of filtration methods and Ultraviolet light technology that together can help keep your system perpetually free of contaminants.
An easy way to improve the air quality in your Buford home? Clean your air ducts. The certified experts at R.S. Andrews take cleaning your air ducts seriously and offer industry-leading skill and technology to ensure your air duct cleaning gets done right! We make a point to provide only the very best to our consumers. Story after story, we deliver smiles!
Are you struggling with asthma or allergies in your own home? Is your ductwork in need of some serious attention? Contact our team today to find out how we can help you best, either online or over the phone at 770-913-6412.
Choose R.S. Andrews for HVAC Service in Buford, GA
When you call R.S. Andrews for service, you can always rest assured you will be in capable hands. Every single one of our technicians has gone through the rigorous NATE (North American Technical Excellence) certification. The R.S. Andrews 100% satisfaction guarantee applies to any job we take, and means that whatever work our technicians do will result in the problem being resolved, fixed for free, or your money will be fully refunded. Your satisfaction will always be our primary goal.
For heating, cooling, or indoor air quality services in Buford, Georgia, contact the professionals at R.S. Andrews.
for Buford, GA
Prompt and competent
Keith - Buford, GA
Highly competent and on time. Technician quickly assessed the difficulty and repaired the water line break. I would use them again.
Great and professional service
Mernoosh - Buford, GA
Professional, caring, and Awesome customer service
Top Notch Service
Kaitlin - Buford, GA
As always - top notch service and speed in resolution of the issue
Response from RS Andrews:
Thank you very much for your review!
Nicole - Buford, GA
Response from RS Andrews:
Thank you very much for your review!
linda - Buford, GA
Response from RS Andrews:
Thank you for your review!
Chris - Buford, GA
RS Andrews is always on time, and the people they send to your house are smart and knowledgable. I have used them for over 5 years now, and I will continue to use them because of the quality of service they provide.
Water leak, Installed new Filter saturated and dirty, Removed cleaned water from aux pan Monitor and balance refrigerant levels Low 112 High 285 SH 12 Sub 8Made Ms wolf aware might need new TXV but system operating properly at time after filter change Ms will keep eye on system and call if issue. Also made aware basement has one main return if want all rooms temperature same need to leave doors open or add returns.
Drain Line Repair HVAC Smiley Diagnostic Club
No basementFound clogged drain flushed out and removed water from drain pan made Cleint aware insulation saturated will keep dripping tell dries out cycled basement system operating properly Refrigerant levels L 113 SH 20 H 324 Sub 10 Found duct work block by items on top made aware could cause damage to duct work Replace air cleaner medias on main and upstairs levels very dirty Rinsed condenser coil on upstairs system suggested chemical cleaning T-Stat set to 66 upstairs unit struggling to keep temperature installed by reliable Made aware appointment under load set at 66? unit running all day will not reach set temperature
Poor cooling, Complaint Upstairs front bedroom (daughter) not getting enough air flow to cool roomOptions #1 Best solution reduct and zone system for total comfort $2895-3876#2 Reconfigure duct work to balance air flow to kids bedrooms $725 ($650 with club) Run new dedicated duct Remove old and cap off Need 1 8" duct run split into 2 6" ducts to bedrooms and secure
No cool, Upstairs system, Found condenser fan motor overheated due to shorted run capacitor system is 13 years old suggested upgradingInstalled new capacitor 35/5 Motor struggling to start Tested Motor running @1.3 amps (1.0 amp max could fail) Found low refrigerant super heat at 42 low signs of leak Recharge and balance refrigerant levels Low 70 psig Superheat 10'F High 212 psig Sub Cool 5'F Cleint aware system leaking refrigerant wants temporary fix **No warranty on refrigerant ** Measure temperature difference 18'F Outdoor temp 86'FClient Aware system needs further attention for permanent fix/repair also made aware system can freeze and leak water causing property damage Suggested upgrading equipment
Furnished, wired, and installed an outlet over the fireplace for a tv. Performed panel maintenance and tightened all connections. Used the customers wood to screw back the Sheetrock that was cut. We are not responsible for patching and painting said Sheetrock.
We furnished, wired, and replaced the smoke detector by the master bedroom on the second floor. The existing one was not sending a signal out, as found out by the home inspector. We tested all smoke detectors and they all work as they should now. We furnished, wired, and installed a bond wire from the main disconnect at the meter, to the gas line. This is to bond the csst as per home inspector.
U/S AC. Found low in freon added 2# of freon with NO warranties. 2.5 ton trane up flow in attic from 1996 recommend replacing system due to age. AC is operating at this time 75 psig at 12*SH.
Removed obstruction from garbage disposal. Tested OK.
Repaired main water service in the ground after meter. Removed PVC 1 foot section and installed PEX pipe with approved adopters. Tested OK.
Opened ceiling where water was dripping through Sheetrock and cabinet to find 1/2 inch copper water pipe feed to toilet had a pin hole leak.Removed section of pipe from leak up to toilet with new shut off valve and supply for toilet. No obvious cause for the leak there was nothing rubbing or touching pipe in this spot.
Came out to inspect grounding system and main electrical panel in home. After inspection determined the grounding system is partially complete and not up to current code. Water system in home is bonded as well as hot and cold sides, ground rods were not installed properly. Installed 2 new ground rods with continuous line to main disconnect to complete grounding system. Inspection of electrical panel found no problems and working properly.
Cabled master bathroom shower drain to clear stoppage. Tested OK.
Completed Air Conditioner preventative maintenance on two units.
Replaced cartridges to lavatory in hallway bathroom and with the customer to show all is good now.Checked pressure to house at 65 lbs.
Estimate for replacement of RHEEM water heater 50 gallon natural gas in garage labor material with expansion tank and water heater pan.Replace fill valve and flapper in two toilets. Install hose clamp on inst hot vent hose $0.00 total for all work.
Completed Air Conditioner preventative maintenance on one unit.
Completed Air Conditioner preventative maintenance on three units.
Estimate to upgrade service to 400 amp re-device of home 4900+ sq ft adding 9 smoke detectors, 1 per bedroom per code, and 1 in garage with living space above per code,and replacing 4 existing smoke detectors that are over 10 years old.
installed 50 gallon natural gas water heater with replacement thermal expansion tank.Removed old water heater for disposal.
Replaced fill valve, flapper and supply Line upstairs hall bath toilet.
customer said too much ice build up on unit had to turn off and remove ice. Found timer on defrost 120 minutes. Inspect defrost board speed up all ok. Removed power to outside unit and reset defrost board to every 30 minute run time. reconnected power. Let unit run 115 and 325 with 9 degree sc . unit operates normal. Did not find any trace of inordinate substance. we had unusual colder than normal weather. inside is non program Honeywell Tstat.
Unit not heating and making a loud noise.Found unit over heating due blower motor seizing up and blower motor wheel coming apart in very bad condition , Also a lot of build up in furnace burner assembly and heat exchanger compartment may cause combustion issues .Tried breaking free motor and tightened blower wheel hub loose/broken won't operate properly will cause over heating.suggested not to operate potential hazard and carbon monoxide detectors. Furnace is 30 years old Recommend upgrading left quote on repair options and upgrading (no guarantee parts available 30 years old).
Free second opinion on replacement of two unit. Found Both units working properly at time .
Warranty call: The gas Furnace Comfort maker is not working Properly on Heat Mode Due to Bad Pressure Switch and Bad ignition module control. The heat mode is working on Short cycling. Due to Aged and conditions I recommend to replaced the gas Furnace ASAP. Note. Costumer is aware of the problems on the unit.