Avondale Estates GA | HVAC Plumbing
R.S. Andrews provides expert HVAC and plumbing service to Avondale Estates GA residents.
Call us now at: (770) 913–6412 or check out why your neighbors call us the top-rated heating, air conditioning and plumbing company in Avondale Estates GA.
for Avondale Estates, GA
Quick and Efficient
Andre - Avondale Estates, GA
Thanks for fitting me in with short notice.
Excellent, timely service
Hoyt - Avondale Estates, GA
RS Andrews has always provided great service, and Jason today continued that tradition
Response from RS Andrews:
Thank you for your review!
No cool, found system overheated due to dirty condenser coil and low refrigerant levels also system has water in emergency drain pan In Attic **Mr didn't want water removed going to have home Warranty company repair aware could cause system failure and/or property damage** Wanted us just to get system cooling for Tenants Approved repairs by phone Started club waived service fee Perform 1 system AC tune up. -Filter:ok -Flush drain line: Flush with h20 and treated *water in pan* -Clean and tighten electrical connections and wires: -Check electrical components: -High voltage wiring Romex -Blower motor: 4.5 amps -Blower cap: 7.5uF @7.1 under load ok -Condenser fan motor: .6 amps -Compressor: 133 amps (16.2 before cleaning) -Dual capacitor: 45/3uF @39.6/2.8 Failed -Contactor: 236 Volts across -Breaker: disconnect box -Recarged refrigerant levels: Low: 73 psig High: 263 psig super heat: 5'F Sub cool: 28'F -Replace valve caps (Missing upon arrival) -Clean
Unclogged tub drain for upstairs guest bathroom. Moen is sending shower mixing valve under manufacturers warranty.
SERVICE CALL NO COOL UPSTAIRS SYSTEM. REPLACED FILTERS ON BOTH SYSTEM. UPSTAIRS EVAP COIL FROZEN. DEICE COIL BY TURNING ON HEAT. RINSED CONDENSOR COIL WATER ONLY. CHECKED REFRIGERANT IN SYSTEM AND FOUND REFRIGERANT LOW. SYSTEM IS 15 YRS OLD CUSTOMER WANT FREON ONLY. ADDED 3lbs R22 UPSTAIRS SYSTEM NO WARRANTY ON REFRIGERANT.
Completed Air Conditioner preventative maintenance one unit.
Completed Air Conditioner preventative maintenance on one unit.
William Washington 2111 .
Augered main sewer line from clean out to clear stoppage. Performed a video inspection of line, found break in line. Estimate on replacing line from clean out to city tap with 4" pvc. waterline with 1" copper from meter to home.Discounting mainline auger.
29 year old furnace not heating. Systems chambers are really rusty did not do camera inspection customer wants to change out furnace instead of replacing gas valve.
Completed furnace preventative maintenance on one unit.
Completed furnace preventative maintenance on two units.
Completed furnace preventative maintenance.
Completed furnace preventative maintenance.Tested all switches,limits, and Heat rise. Quote to install condensate pan treatment.
Completed furnace preventative maintenance. Changed filter Customer provided. Checked all safety and wiring connections. Checked blower speed and did camera inspection.
Completed furnace preventative maintenance.Changed filter.Tested switches and components. Activated steam humidifier.
Performed two unit maintenance .Inspect all Motors and electrical.Also Cycled the system. Add single pole Contractor and pan treatments. Flushed the drain lines with one gallon cleaner each attic drain. Replaced Two 16x26x1 filters .
HVAC technician to program thermostat for customer and taught him how to do it as well.
Plumbing : Plumber to rebuild for master bathroom toilet tank by replacing fill valve, flapper, toilet handle, and supply line.
HVAC technician to repair no cool ac unit.
Preventive Maintenance on HVAC unit.
Preventive maintenance on HVAC, replaced mpg refill
Preventive Maintenance on HVAC system
Preventive Maintenance on HVAC system