Conyers GA | HVAC Plumbing
R.S. Andrews provides expert HVAC and plumbing service to Conyers GA residents.
Call us now at: (770) 913–6412 or check out why your neighbors call us the top-rated heating, air conditioning and plumbing company in Conyers GA.
for Conyers, GA
Slab Water Leak
Robert - Conyers, GA 30094
Furnished, wired, and replaced the outlet in the family room as per electrical issue #7.3(1) Rewired outlet in the master bedroom closet as per electrical issue #7.3(2) Furnished and installed bulbs in the master closet, rear patio, and flood light at the back of the house as per electrical issue #7.3(3) Rewired the switches and installed a blank at one location in the family room as per customer and electrical issue #7.3(4) RS Andrews assumes no responsibility for the existing wiring. Furnished and installed a cover plate in the attic as per electrical issue #7.3(5)
smiley advantage club diagnostic 59.00..,refrigerant 198.00..,dual motor run/compressor start device w/ 5 year warranty 349.00..,smiley advantage club maintenance membership 227.00.., ***********************comprehensive hcfc leak detection will be performed on next maintenance visit/HP n/c**************************
SERVICE CALL NO COOL. TWO SYSTEM NOT WORKING. UPSTAIRS SYSTEM CHECKED AND FOUND GROUNDED COMPRESSOR ON AC. MUST REPLACE DUE TO AGE AND CONDITIONS. DOWNSTAIRS SYSTEM CONDENSOR FAN MOTOR NOT WORKING. TWO AC UNIT SAME SIZE ON TONNAGE. REPLACED DOWNSTAIRS CONDENSOR FAN MOTOR WITH THE UPSTAIRS CONDENSOR FAN MOTOR. LABOR ONLY TO SWAP PARTS. CHECKED CAPACITOR PART IS GOOD. QUOTE TO REPLACE UPSTAIRS EVAP COIL AND AC. LENNOX BRAND 2TON 14SEER XC $4483 14SEER ACX $4074
Installed meter nipple, check valve, tee and ball valve alone with waterline from meter to home in 3/4" copper. tested no leaks found. ** 350.00 to tie irrigation system into waterline **. 50.00 per irrigation line repair 3 year warranty **Not responsible for irrigation repair. ( homeowner opted to repair )
Customer has a pump floor irrigation system that requires electrician also has some live wires. We troubleshot irrigation system panel not having power.
customer wass having national leak detection for slab leak in home.
non ac unit n/c 11-12 yrs d/s
William 2111 .
Leak located by leak detection, homeowner still uncovering line massive roots. Homeowner will call once line is exposed .
Unit sensor very dirty. Causing burners to cycle. Cleaned sensor system and needs duct cleaning.
Install lennox 5 ton drv furnace only in crawl space 24" wide 80% 135k btu.
Estimate to replace shower hot&cold stems and 3/4 pressure regulator valve pressure to house is reading at 125 psi,psi should be reading at 25 to 75 psi.
Estimate to installed 40 gallons natural gas water heater and 2 gallons expansion tank with 1 years warranty on parts and labor 6 years manufacturers warranty.
Installed lennox 80% 90k btus complete duel fuel system in attic up-flow 3 ton 14hpx filter rack. Brought vent up to code.
Pressure switch sticks got it to temporary reset, igniter is weak may fail, and gas line is not up to code.
Found thermostat faulty keeps changing temperature and reading low battery even with new batteries installed. Gave customer a quote to replace
Estimate to replace tub and shower valve. Remove master bathroom lavatory cabinet with sink and reconnect lavatory cabinet ,sink and toilet.
Replaced ignition board.
install lennox furnace only in garage upflow 14" wide 80% 70k btus new lennox comfort sense 7500 stat.
Leaks on master bathroom 1st lavatory faucet .
Checked inside and outside home. Found no obvious leaks,but meter indicates a leak either underground or under the slab, his pipes come up under water heater in garage ranch state home no basement or crawl space. Customer needs to contact American leak locate to check slab for possible leak .
Air conditioner has a condensation leaking. supply plenum not sealed and cool air leaking inside wall which caused black spots on wall. Removed insulation from inside old coil housing wrapped with bubble wrap insulation for inside coil box.
Customer had second testator on zone system turned "OFF" .
Found system low of refrigerant r-22 owner wants quote to replace system scheduled.
Completed Furnace preventive maintenance.Devices and condensors need to return with helper to recheck low voltage wiring for downstairs system
Replaced filter checked heat ex changer venting burners.Safety heat check complete system operating properly