Norcross’s HVAC Company
Choose R.S. Andrews for Heating & Cooling Services in Norcross
Imagine your Norcross home without heating or cooling. Not too comfortable, right? That’s where R.S. Andrews can help. We are the area’s leading HVAC experts—so you can rest easy knowing a professional is on the job when any of your home systems break down or if you just need to replace old, malfunctioning equipment.
When you need a new HVAC system installed or an older system replaced, count on the professionals at R.S. Andrews. We’ve been working with HVAC systems throughout Norcross for more than 50 years—contact us!
HVAC Installation in Norcross
New HVAC installations present a wide variety of options that can save you money on your power bills and reduce the amount of HVAC maintenance and service that will ultimately be required over the life of your new unit. If you want to upgrade your existing system instead, options like adding heat pumps, two-stage furnaces, air-to-heat exchangers (HRVs), and programmable thermostats can all go a long way toward increasing efficiency and extending the life expectancy of your system.
No matter the HVAC system/product you need installed in Norcross, R.S. Andrews can help. We have experience installing:
For all your HVAC installation needs in the Norcross area, choose R.S. Andrews. Contact us today!
Heating & Cooling Maintenance in Norcross
In order to get the most out of your equipment, we highly recommend regular HVAC maintenance. Many times, small timely adjustments and filter changes that are done on a regular basis can wind up saving you from breakdowns that always seem to occur right when you need your system the most.
Trust R.S. Andrews for high quality HVAC maintenance for the following systems in Norcross:
The Smiley Advantage Maintenance Plan
Our technicians estimate that 82 percent of the repairs they see may have been eliminated or reduced by a regular tune-up program. Changing your air filters monthly is a step in the right direction, but it just isn’t enough. Modern HVAC systems have an advanced electronic system which requires cleaning and inspection from the inside out to ensure that every piece is properly calibrated and running efficiently – a task best left to a trained professional. Click here to learn about the benefits of our Smiley Advantage Plan.
Call R.S. Andrews at 770-913-6412, and one of our HVAC professionals will be happy to answer any and all of your HVAC questions and fulfill whatever needs you have for your HVAC system.
HVAC System Repair in Norcross
There’s nothing worse than an inoperable heating or cooling system. They never seem to give out at a time that would be convenient for you, don’t you think? You air conditioner will probably break on the hottest day of the year, and vice versa for your heating system. For reliable HVAC repair in Norcross, you can count on R.S. Andrews.
Our team has experience repairing the following systems:
Contact R.S. Andrews for HVAC repair—no matter the time or day, you can count on us. We provide 24 hour emergency HVAC repair in Norcross.
Indoor Air Quality in Norcross
We’ve found that many homes in Norcross face significant indoor air quality issues as a result of the seasonal high humidity in our area, which creates conditions ripe for mold and mildew growth in both old and new HVAC systems. Our HVAC technicians can help you determine which strategies will work best for neutralizing airborne particulates in your Norcross home, which often involves a combination of filtration methods and Ultraviolet light technology that together can help keep your system perpetually free of contaminants.
An easy way to improve the air quality in your Norcross home? Clean your air ducts. The certified experts at R.S. Andrews take cleaning your air ducts seriously and offer industry-leading skill and technology to ensure your air duct cleaning gets done right! We make a point to provide only the very best to our consumers. Story after story, we deliver smiles!
Are you struggling with asthma or allergies in your own home? Is your ductwork in need of some serious attention? Contact our team today to find out how we can help you best, either online or over the phone at 770-913-6412.
Choose R.S. Andrews for HVAC Service in Norcross, GA
When you call R.S. Andrews for service, you can always rest assured you will be in capable hands. Every single one of our technicians has gone through the rigorous NATE (North American Technical Excellence) certification. The R.S. Andrews 100% satisfaction guarantee applies to any job we take, and means that whatever work our technicians do will result in the problem being resolved, fixed for free, or your money will be fully refunded. Your satisfaction will always be our primary goal.
For heating, cooling, or indoor air quality services in Norcross, Georgia, contact the professionals at R.S. Andrews.
for Norcross, GA
Great service and competitive price.
Greg - Norcross, GA 30092
I solicited two bids and RS Andrews was slightly lower, but the service was excellent. They worked with me on the timing of the job and finished the work quickly.
Good People, Good Service
Pat - Norcross, GA 30071
My main electrician, Chris, is awesome. He takes care of things quietly and quickly and only does the work requested. If he notices anything that looks like it's getting old or sketchy, he'll alert me to it. Early on Chris had help from an individual who made several mistakes, requiring a call back. Chris corrected them quickly and easily.
Nicole - Norcross, GA 30092
Response from RS Andrews:
Thank you for your review !! 🙂
Prompt and friendly service.
Tim - Norcross, GA 30093
This technician has been here before. As always he did a great job.
Response from RS Andrews:
Thanks for you review!
Sue - Norcross, GA 30092
Response from RS Andrews:
Thank you for your review!
Peachy - Norcross, GA 30093
Original service appointment was mysteriously lost in the computer; wasted an entire day waiting. When service tech arrived the next day he was prompt, courteous, and very knowledgable.
Response from RS Andrews:
Thank you for review!
GB - Norcross, GA 30093
Very knowledgeable technician. Good advice and recommendations to prevent future issues. I would recommend R.S. Andrews to all homeowners.
Response from RS Andrews:
Thank you for your review!
Wow-great service at short notice
Dallan - Norcross, GA 30092
Showing up only an hour or two after the call and fixing the problem right there--no, let me pick up the part and charge you for a second visit. Great service!!!
Great Service as usual from Oscar
Bruce - Norcross, GA 30092
Oscar does a complete and thorough job every time he services our equipment
Poor cooling, System running ck and test all components. **Found return leak system pulling in attic air **Need to sch install to return and seal air cleaner. -Filter: ck media ok -Clean and tighten electrical connections and wires: -Check electrical components: -High voltage wiring -Blower motor: 1.6 amps -Condenser fan motor: .65 amps -Compressor: 10.2 amps -Dual capacitor: 45/5 uF ok -Contactor: 239 Volts across -Breaker: amp -Balance refrigerant levels: Low: 147 psig High: 335 psig super heat: 7 'F Sub cool: 6 'F -Check condenser coil -Evaporator coil : ok -Check duct work: return leaking -Measure temperature difference: before 15'F after 19'F -Outdoor ambient temperature: 90'F -Cycle system, operating properly at this time
Installed new 50 amp feed from main panel in garage of home to new office in backyard. Installed new pipe in ground from main house to new office. New office has a main disconnect and ground system installed. Installed new 125 amp rated, 50 amp fed, sub-panel in office. Installed 3, 20 amp, arc-fault/GFI protected circuits in new office. Installed a total of 9 receptacles in office, including floor outlet and exterior receptacle. Installed 4 new lights that customer provided. Installed 30 amp feed for future A/C unit. Currently installed on a 20 amp breaker. Wire is capable of 30 amps however. Installed all receptacles and switches as well. Extra: Changed out unlisted breakers in panel to correctly listed breakers for panel enclosure. Panel is overloaded however by 7 circuits. Had removed $195 from price and covered permit cost in cost of project since customer trenched and moved office closer.
Customer's AC disconnect was burned apart at the A phase. - Possible loose connection or lightning strike. Installed new SquareD QO 100 amp sub panel for AC units. Installed 2 2 pole 20amp breakers for the AC's. Powered up both AC's. - Downstairs condenser is running and upstairs is not as expected by homeowner. Discussed whole home surge protection to possibly be installed at a later date at $379.00
Upstairs unit was not cooling properly do to a few issues. Running high head pressure and having a dirty coil makes for a low efficient system. We have cleaned coils and replaced 2-16x25x1 filters. We must come back to check pressures. Disconnect box is damaged and wont turn on units. Once we get power at that point we can determine if unit needs refrigerant. At this time units are both not cooling until electrical issue is handled.
The drain for this system was stopped up. Tech cleaned the line and made sure they are easy to service in the future. The Refrigerant level is good.
replaced both upstairs tub and shower faucet cartridges. Customer has financing.
tightened all connections in panel and tested loads. changed out unlisted breakers to cutler hammer CL breakers to correct unlisted issue. performed diagnostic work on refrigerator circuit and back door switch/light not working. replaced bad switch at back door, and found loose connection to refrigerator. installed customer supplied ceiling fixture in breakfast area. installed ceiling fan bracing in dining room area, and replaced ceiling fan with customer supplied ceiling fan. installed blank plate on back door receptacle.
installed 5 switched receptacles installed 40A 3-pole GE breaker
Perform smiley preventive maintenance inspection 1 system AC tune up. 1 of 2 bisits. added 2# of freon with NO warranties. -Filter: 14"25"1" -Flush drain line: needs EZT and wet switch -Clean and tighten electrical connections and wires: -Check electrical components: -High voltage wiring -Blower motor:??xx amps -Condenser fan motor: .60 amps. -Compressor: 9 amps. -Dual capacitor: 30/5uF -Contactor: 241Volts across -Breaker: 60 amp -Monitor refrigerant levels: ???Low: 70psi High: 220psi super heat: x10'F Sub cool: 10'F -Rinsed out condenser coil -Evaporator coil: 20plus years old. -Inspect flue/vent pipe: -Check gas valve and gas line: -Check duct work:???? -Measure temperature difference:20* -Outdoor ambient temperature: 91*'F -Cycle system operating at this time but is 20 plus years old and anything may go out at anytime. ??*Equipment normal wear and tear
upstairs unit not cooling found compressor not running due to bad capacitor, replaced 40/5 cap, cleaned condenser coil an ran unit finding unit only running 105/245 with a 30 degree super heat so added 1lb of 410a system is now running ok
120V 20A circuit extension with box and receptacle
SERVICE REPAIRED: The 3 1/2 Ton AC system Trane 6 Years old was not working properly due to poor maintenance condition. service Performend, Clean Condens Coil with Chemical plus Add one Pound of refrigerant R 410a, Test Cooling mode, check refrigerant charge the pressures are 125/305 psi with 8 degrees Subcooling. After final inspection system is working properly. I recommend to service the system at least 2 times a year to keep the system at the Highest efficiency possible and extend the life of the Equipment.
checked filters. Advised Cust of filters needed. checked pr assures on both systems. upstairs system is a little low on freon added 1.5 lbs of r22
replace hot side shut off valve for washer machine box card on file
1-Replace 40 gal natural gas water heater with a 50 gal natural gas water,upgrade gas line,install new gas valve and one for water shut off. 2- Removed one piece toilet from upstairs bathroom and installed new toilet provided by customer.Toilet removed to be installed at customer mothers house. 3- Installed new hose bib in front of house . 4- installed new washing machine box at mothers house, and toilet removed from other house.
Installed customer provide 1/2 hp garbage disposal.
When toilet is flushed the water bubbles on the other side, tried to plunge the toilet and it came out of the sink womens and mens restroom. Bath Cable / Men's -and- ladies restroom > Commercial Diagnostic > Pull and Reset Toilet (ONLY)
non club water leak
Completed One time tune up with Angie's List Coupon on one unit.
Replaced wax ring and toilet bolts by pulling and resetting the toilet.
James Anglin 1510 .
Air conditioner not cooling. Traced problem back to a bad run capacitor. Replaced and checked operation. Unit operating properly at this time.
installed a 20 amp 120 volt circuit from the panel in garage to the microwave in the basement.performed panel maintenance and tightened all connections.
Air conditioner not cooling because system shut down due to clogged drain line which set off flood protection switch. Also found crack in existing vinyl tubing cut out section and replaced made Mr aware may need to run new drain line if cracks again it is very brittle Showed section Mr going to keep eye on it will call if wants drain tubing replaced.Cycled system operating at time.
Completed Air Conditioner preventative maintenance on one unit. Installing new full Lennox system 3.5 ton XC14 and 90,000 BTU SL280V with 10 year parts and labor warranty including t-stat and 1 year maintenance on 1 system.
Clear main sewer line for complex from the clean out in the parking lot. line blockage was 120 ft out from the first clean out 20 ft from the second line cleared with 3/4 cable.