Lithonia GA | HVAC Plumbing
R.S. Andrews provides expert HVAC and plumbing service to Lithonia GA residents.
Call us now at: (770) 913–6412 or check out why your neighbors call us the top-rated heating, air conditioning and plumbing company in Lithonia GA.
for Lithonia, GA
Service was great!
Toby - Lithonia, GA 30058-5423
R.S. Andrews has some very skillful technicians. Not ony are they skillful, but they are punctual, pleasant and smooth mannered. I really appreciate them for the clean-up after they have completed the job. KEEP UP THE GOOD WORK!!!!!
Excellant service, affordable pricing!
Andrea - Lithonia, GA 30058-2913
Professional and fast
Keith - Lithonia, GA 30038
Good people and great service
Response from RS Andrews:
Thank you for taking time out of your day to complete our review!
Excellent professional instalation.
Joseph - Lithonia, GA 30038
Like the idea of separate 2 man crews for HVAC & water heater. Questions were answered quickly. Everything mentioned in estimate was done.
Great customer service and technical expertise
Ashiti - Lithonia, GA 30038
the cust service rep was great. The technician was great. My only bone to pick is pricing was a bit high
Raye - Lithonia, GA 30058
Always consistent with appointments over the years.
Leak Search Level 01 Repairs Leak on 3/4" copper waterline supplying hot water for kitchen faucet and dishwasher. Opened cabinet under kitchen sink to locate leak. Cut out leaking section of copper. Installed new 3/4" copper, emergency stop for dishwasher and faucet. Installed new supply line on hot side for kitchen faucet. Tested, no leaks found at this time.
installed customer supply lavatory faucet and enlongated toilet seat in master bathroom
Removed failed main water pressure regulator in basement. Water pressure before 75psi. Installed new main water pressure regulator. New water pressure 60 PSI. Calibrated existing thermal expansion tank to 55 psi. Tested ok.
Opened drywall in cieling , located break on 1/2" cpvc waterline in cieling. Open access holes in cieling and in adjacent wall. Cut out broken section of 1/2" cpvc. Repaired break with two 1/2" couplings and a 1/2" 90*. Pressure on home at 120psi, installed 3/4" Pressure Regulator Valve to reduce pressure in home. Waterheater saturated with water and drywall Recomend replacing. Customer request to be billed
SERVICE CALL UPSTAIRS SYSTEM NOT COOLING PROPERLY. FOUND REFRIGERANT PRESSURE HIGH. CONDENSOR COIL CLOGGED. CLEANED CONDENSOR COIL WITH CHEMICAL SOLUTION. ADDED 2lbs R22. SYSTEM MAY HAVE SMALL LEAK IN REFRIGERANT. NEED SMILEY CLUB PLAN TO SERVICE BOTH SYSTEMS
No cool water coming from bottom 1 sys hallway closet 4 y/o. 410a refrigerant 267.00.., ************************will perform leak detection service on maintenance visit due to time constraints today************************
Came out, replaced 3 can lights in basement main area. Replaced and working properly. Secured can light trims on existing fixtures and checked integrity. Recommend few other can be changed at Cust earliest convenience.
non club install water filtration sys (cust supplied) , Tony to complete repairs.
non club ac sys attic not cooling/2yo
Reset super heat sub cool rate.
Completed one time tune up on two units.
Completed one time up on two units.
Completed Air Conditioner preventative maintenance on three
William Washington 2111 .
Installed hall customer supplied lav faucet and pop-up.
William Washington 2111 .
Rheem 50 gallon gas Water heater leaking. Waterheater needs to be replaced. Waterheater will need to be moved due to increased width of new waterheaters. The current space is 20" in width. A new waterheater stand, pan and drain will need to be installed.1/2" black iron will need to be piped over to waterheater. Thermal Expansion tank will need to be installed. 3/4" ball valve will need to be installed . Waterheater vent will need to be reworked. Waterheater will extend past existing space for furnace and waterheater and into garage parking.
William Washington 2111 .
Installed 3/4" pressure regulator valve and ball valve in garage. Set prv at 70 psi. Installed thermal expansion tank and ball valve at water heater. T&P dripping slightly at back of home, may be from existing water in line. If slow drip persist we will replace T&P .
Heat repair. Traced problem back to plugged filter. Cleaned flame sensor and checked run cap. Replaced filter. Unit is operating properly at this time.
Customer need inducer assembly.
Need inducer assembly.
No heat Warranty call new system installed 6/6/15. Found unit not changing over to auxiliary heat automatically due to bad wire in Low Voltage wiring to outdoor sensor run new and rewired. Set up thermostat to operate dual fuel system and switch from Heat-pump to gas for efficiency. Installed new outdoor sensor.
SERVICE CALL RETURN VISIT. REPLACED 3 TON EVAPORATOR COIL ON AIR HANDLER IN ATTIC. RECONNECTED PVC DRAIN AND INSULATED SUCTION PIPE. ADDED
Repaired gasoline to furnace in attic, installed gas valve ,nipple and gas flex.
Installed 1/2" hose bib on washing machine hot side.Tested no leaks found. 1 year parts and labor warranty
Water in filter rack and furnace cut off. Found water in 3/4 PVC drain. Float switch in up postion causing equipment shut off. Explained if the AC is turned in winter the Evaporator will freeze. Heat rise 45f, Gas pressure 3.5 WC, Blower motor 3 amps, inducer .68WC. At this time the furnace function normal. Replaced batteries in thermostat read weak battery and replaced 14/25/1 pleat filter. MOTILI: BILL OUT
SERVICE CALL NO HEAT. UPSTAIRS FURNACE CANT PROVE A FLAME. CLEANED FLAME SENSORS ON ALL THREE SYSTEMS. FURNACE WORKING PROPERLY AT THIS TIME. RECOMMEND SMILEY CLUB FOR ALL THREE SYSTEMS.