Loganville GA | HVAC Plumbing
R.S. Andrews provides expert HVAC and plumbing service to Loganville GA residents.
Call us now at: (770) 913–6412 or check out why your neighbors call us the top-rated heating, air conditioning and plumbing company in Loganville GA.
for Loganville, GA
Troubleshot pump power. Found power correct at pump and everything tight. Found meter flashing unusually. Power company will send a crew out to check their meter.
When tech arrived found condenser with burned contact or replaced contact or checked furnace, new filter checked pressures.
System not able to keep up do to being low on refrigerant. We have re-charged system and unit is now cooling properly. Charged up with 2 pounds of 410 A Puron. We rinsed off coil with water for better efficiency. Customer has purchased maintenance plan and we will continue to monitor system performance. If unit leaks again we may have to do a leak search. There is no warranty on refrigerant and if unit does have a leak we cannot guarantee how long it will cool properly. When we do the maintenance visits we can determine if unit needs additional work. Customer has replaced his own filter 1-20x20x1.Today's refrigerant pressures.Low= 160 High= 250 Super heat= 10' Subcool= 12'System temperature differential is 19 degrees within specs.
installed American standard 10" rough enlongated toilet in basement bathroom with 1 years warranty on parts and labor
upstairs downstairs leak; found escution sleeve behind tub and shower faucet handle with a gap of 1/2 inch.Removed trim plate and shimmed valve back in wall and sealed around trim plate and tub spout. Customer to monitor, if problem persists will warranty service call only.Would need to remove Sheetrock to find leak.
Estimate to replace 40 gallon natural gas water heater in upstairs closet labor and material.
Water collecting in emergency drain pan. Found where drain line connects to coil broke off. Not repairable coil pan has crack in it also. Coil pan needs to be replaced.
Two units not working.Found that both units were missing igniters, when replaced igniters found that main level units smart valve would not turn on inducer an upstairs unit would light pilot but not open gas valve units should just be replace due to age an cost of valves.
Second opinion on non working furnace.Found igniter missing off both units will need igniter to get unit to run.
Estimate to move sewer lines higher in ceiling, moving water heater, providing drops for toilet, shower and lav sink in basement bathroom.
Completed furnace preventative maintenance on one unit.
completed furnace preventative maintenance on one unit.
Completed furnace preventative maintenance.
SERVICE CALL: THE SECOND FLOOR AC SYSTEM WAS NOT WORKING PROPERLY DUE TO POOR MAINTENANCE CONDITION.MAIN DRAIN LINE WAS CLOG UP, LOW REFRIGERANT CHARGE, DIRTY CONDENSER COIL,AUXILIARY DRAIN PAN WAS FULL OFF WATER. REMOVED ALL THE WATER PLUS CLEAN DRAIN LINES. DUE TO AGED AND CONDITIONS I RECOMMEND TO REPLACED THE SYSTEM.
Installed faucet in upstairs bathroom.
Completed air conditioner preventative maintenance furnace located in attic and takes 1-20x25x1 filter. Flushed drain line and checked all air conditioner components. Replaced Contractor on Ac unit and tested. System is cooling properly. Pressures and components looking great. Found no other issues at this time.
Completed furnace preventative maintenance on Air handler located in attic. Replaced one 16x20x1. Checked all heat components and found no issues.
Preventative maintenance on one air conditioner.
Relight pilot light.
Checked system pressures and found no issues. Thermostat is located in hallway and is hot due to attic fan. Recommended having system upgraded and new duct work for better performance.
Performed preventative maintenance on one ac unit. Checked all ac components and found unit operating properly.
HVAC technician to repair no cool ac unit.