Snellville GA | HVAC Plumbing
R.S. Andrews provides expert HVAC and plumbing service to Snellville GA residents.
Call us now at: (770) 913–6412 or check out why your neighbors call us the top-rated heating, air conditioning and plumbing company in Snellville GA.
for Snellville, GA
Great price for the service. Was exactly on time.
Jennifer - Snellville, GA 30039
Jason went quietly about his work. He reported what he found, made suggestions. I was impressed.
Response from RS Andrews:
Thank you for taking your time and completing the review!
We furnished, wired, and Installed a breaker to separate double tapped breaker code violation. We separated the neutrals as required by code since they were multiple wires per screw. We furnished, wired, and replaced a tandem breaker as required by code since it was over-sized and the wrong type. We furnished and installed 2 connectors on wires coming into the panel as required by code.
Service fee call. Performed panel maintenance and tightened all connections.
We furnished, wired, and replaced the 2 lights at the back of the home with 175 watt equivalent LED floodlights. Troubleshot 2 outlets, 1 per sons room, that had no neutral. Furnished, wired, and replaced said outlets as the wires were loose. Outlets work as they should now.
replace American diverted stem for 3 handle tub and shower valve also unclog tub drain line as well for guest bathroom
1- replaced leaky angle stop under kitchen sink. hot side. 2- replaced PRV Valve.
ac unit wasn't cooling found compressor an fan motor not coming on due to bad capacitor, replaced 40/5 cap an started unit an everything checks out ok
Troubleshot fan in the living room. Found fan installed on a non fan rated box. Removed fan as it is improperly installed and can fall. Troubleshot fan in the upstairs bedroom. Found fan installed on a non fan rated box. Removed fan as it is improperly installed and can fall. Troubleshot fan in the upstairs bedroom. Found fan installed on a non fan rated box. Removed fan as it is improperly installed and can fall.
Replaced hall bath toilet with Kohler high line.
Customer took garbage disposal apart and kitchen faucet leaking. Re-work plumbing drain configuration under k/s END TASKS*/
Estimate to install a switch and switch leg in the kitchen by the sink area for under cabinet lighting,customer provided puck lights,a switch, switch leg in the kitchen by the microwave for under cabinet lighting, customer provided puck lights, and a new wire and box to relocate light above the island in the kitchen.
Completed Air Conditioner preventative maintenance on two units.
Estimate on replacing Tub and Shower Valve.
Estimate to installed 1/2 gas line with gas valve for gas stove must run gas line in crawl space.
Return from preventative maintenance visit and install attic tent staircase to attic and close.
Completed furnace preventative maintenance on one unit.
Estimate to replace 50 gallons natural gas water heater 2 gallons expansion tank and 3/4 pressure regulator valve.
Furnace not heating. Found system in attic has zone system. Air handler is running on heat strips only. When temp outside is low heat strips alone can not keep up with temp in home. Heat-pump not running due to low freon.
Installed new customer supplied burner assembly and re-lit water heater. Tested OK.
Furnace no heat on main level unit.Found relay in gas valve giving problems closing, valve gets 27 volts just have to play with wires to get to stay on
SERVICE CALL: bathe Gas furnace York is 16 Years old was not working properly due to lack of maintenance on the Unit. Flame sensors was full of carbon build up plus inducer motor is overheating. Performed one time tune up clean flame sensor, filter is ok, test heat mode, test all safety components. Due to Aged And Conditions I recommend to Upgrade the system.
Located leak in yard at meter. Cut out broken (sharkbite fitting ) 3/4" female sharkbite used as transition fitting from cpvc to pvc. Installed 3/4" cpvc FIP. tested no leaks found. Back filled waterline .
Repaired drain hose for dishwasher under warranty.
Replaced kohler flush valve seal for downstairs 1/2 bathroom toilet.
Completed one time tune up on two systems.